PV Wire, PV Cable, 8 AWG, 19 STRBC, 2KV, Red, Per FootStandards:
Underwriters Laboratories Standards UL-4703, UL-854
UL 1685-FT4/IEEE 1202 ICEA T-29-520 NEMA WC70/ICEA S-95-658
NFPA 70: National Electrical Code (NEC) ARRA 2009; Section 1605 Buy American Compliant
Stranded conductors, uncoated copper per ASTM-B787 and ASTM-B8
Cross-linked polyethylene (XLPE) insulation per UL-854
Type Photovoltaic copper conductors are suitable for outdoor rooftop applications without conduit and for use in conduits and
raceways installed underground in conduit in wet locations, and where condensation and moisture accumulations within the
conduit do not exceed 90C. Applications requiring direct burial is permitted for Type Photovoltaic per UL-854. Applications
requiring type Photovoltaic conductor, temperatures shall not exceed 90C in wet or dry locations.
Available in 600V and 1000V/2000V. All cables comply with ULs VW-1 (Vertical Wire) Flame Test. Insulation compounds are rated for flame and sunlight-resistance in all sizes and colors.